Hofmann (Beijing) Engineering Technology Co.,Ltd
Add:6F, East International Building, No.2 DongZhiMen Outside Street, DongCheng District, Beijing
Plate heat exchangers are a type of equipment that requires high safety. When the gasket is damaged, the external drip is obvious. The heat exchanger will start with a slight leak at the beginning. In process equipment with high pressure shocks, large leaks may occur due to gasket damage. Its service life has an important influence on the service life of the plate heat exchanger. If the seal heat hardens and loses its original elasticity, the heat exchanger will not work properly.
The joint surface of the plate heat exchanger should be cleaned with a chemical cleaner. Also, it is necessary to use a chemical cleaner to remove the softener and anti-blocking coating adhered to the gasket. Apply the adhesive to the middle of each bonding joint surface. Depending on the width of the gasket, the width of the adhesive is about the width of a match, and then the adhesive is applied to the entire bonding surface by a brush to average Make full use of the entire joint surface. Depending on the type of adhesive, wait for a certain amount of air drying time, then put in a gasket, stack the various plate heat exchangers together, tighten with a tensioning screw, or press the weight on the stack. On the heat pack. Depending on the type of adhesive, the hardening time is about 8-20 hours. For blending adhesives, screw tightening and furnace heat hardening are necessary.
The softening of the elastomeric gasket is related to pressure and temperature. When the gasket loses its elasticity, the heat exchanger will leak. In some products, in order to solve the dripping phenomenon caused by the aging of the gasket, the heat exchanger should be adjusted for the sealing function, that is, the bolts of the combined plate heat exchanger are tightened again. Adjust the pressing force of the elastic gasket between each heat exchanger to solve the dripping problem. On the nameplate of a heat exchanger with this function, the maximum and minimum stresses are generally given. For new heat exchanger sets, the connection should be fixed with the minimum allowable stress. Depending on the number of heat exchanger sheets per set, the tightening force of the heat exchanger can be adjusted one or more times. Each time you tighten, you can screw the nut into the 3mm and always pay attention to the stress of the adjustment piece during the tightening process. Moreover, only the heat exchanger that has no working pressure is required to adjust the tightening force at room temperature to prevent dripping.